Logano plus GB applications manual 1 Technical specifications Buderus can not be held responsible for such poten. tially detrimental effects. Buderus GB Innovative Technology. The gas fired condensing GB boiler offers innovative technology in a compact, robust form with simple. Buderus Logano plus GB Pdf User Manuals. View online or download Buderus Logano plus GB Installation Manual.
|Published (Last):||5 October 2014|
|PDF File Size:||6.57 Mb|
|ePub File Size:||6.29 Mb|
|Price:||Free* [*Free Regsitration Required]|
The thermal insulation reduces energy losses. Standards And Directives Insert the test probe through the test port into the core flow inside the flue. Installing The Buderud Drain Completing Inspection Or Maintenance In An Emergency If the storage tank will be installed in Massachusetts, it must be installed by an installer or dealer who is registered there.
Massachusetts Installations Only Boiler size [kW] Fig. Operating faults through power failure! Installing Gas Feed bbuderus Heating System Water Quality To print the manual completely, please, download it.
Making The Electrical Connection Page 3 List of keywords Recognising And Resetting Faults Check gas train function. Page 5 B Maintenance and repairs may only be carried out by an authorised contractor.
BUDERUS LOGANO PLUS GB INSTALLATION AND MAINTENANCE INSTRUCTIONS MANUAL Pdf Download.
Observe the national regulations. Cleaning The Burner This would result in a fault shutdown. B Never operate this boiler as a gravity-fed or as open vented heating system. Action In An Emergency Carrying Out A Leak Test plis Page 43 – Cleaning the burner and heat exchanger Page 44 Page 45 Page 46 Page 47 – Checking gas valve for leaks Page 48 – Checking for leaks during normal operati Turning The Heating System Off Tools, Gg312 And Auxiliary Equipment B Confirm the tightness test with an entry into the commissioning report Chapter 6.
Buderus Logano plus GB312 Installation And Service Instructions Manual
Checking Appliance Equipment Under Full Load Comments to this Lgano Your Name. B Close the flap on the RC35 programming unit.
Replace SAFe Perform reset!
Checking For Leaks During Operation The boiler block transfers the heat generated by the burner to buderys heating water. Table of contents Table Of Contents The directions of this installation and maintenance. Levelling The Boiler Vertically Page 66 Check water pressure Replace water pressure short circuit.
Shutting Down The Heating System If the CO content deviates by more than 0.
Testing The Gas Supply Pressure Wet Cleaning The Heat Exchanger B Ensure that the sealing washer with gasket is seated in the locking cap. Heating System Inspection Check the voltage at the Replace the SAFe in temperature sensor case of deviations. Commissioning B Prior to commissioning, check the operating pressure of the heating system on the water side ggb312 adjust if required. Table 17 1 The gas supply company must guarantee the min.
Installing Jacket Panels Purging The Gas Line Fitting The Cover B Push the control unit cover down into the guide rails. Servicing And Maintenance Logs B First hook in the bottom of the front panel , then raise slightly and hook in at the top. Replace low pressure switch available separately Pous. Inspection And Maintenance Transporting The Boiler On Rollers